Is ist possible to downgrade a controller with CODESYS Control for PFC 200 from 184.108.40.206 to 220.127.116.11?
When I update the controller with 18.104.22.168 to 22.214.171.124 then it says update finished. (see pic)
After the update the controller is no more reachable so I have to reboot it. Thats ok.
But after the reboot it still has version 126.96.36.199 again.
on runtime side I always would recommend to use current version (securiy update included & many bugfixes etc)
Even if you decide to work in CODESYS with 3.5SP9/SP10 whatever, it is safe to use
Wago Firmware 10 and CODESYS Runtime 3.5SP11Patchx.
(Just install the ipk of the runtime to the PFC200 controller )- if you do this I would even not install the SP11 PFC200 Package into your
SP10/SP10 CODESYS / Package Manager
- just use everything in our selected version - only use the ipk our of the store download.
The question came up when I wanted to simulate a behavior of a customers machine. This machine was with an older package, so I had to downgrade my test station, because the package version was interesting.
I restored the Wago firmware over an SD card and the applicated the version I needed. This way is just not nice and costs time.
important commands are:
install older Version
ipkg install codesyscontrol_arm_pfc200_V3.5.x.x.ipk
Log in to post a comment.