Is posible to connect Codesys with BeagleBone Black with a Profinet dispositive? And if it is posible how can I do?
I see a Profinet network in available devices.
Rightclick on Device (your Beaglebone) => Add Device => Profinet IO => Ethernet Adapter => Ethernet => add device => close window
Right click on Ethernet => Add Device => Profinet IO => add what you want: IO Device if BBB is a slave or IO Master if BBB is a master => add device => close window
Right click on new added device => Add Device => add your IO, Drives which was previously registered in Tools=>Device Repository
Is this what you are looking for?
there is one little problem doing profinet on BBB.
Think the internal networkcard does not work.
You need to test it with a usb to ethercat Adapter.
I connected the BBB like Master with Ethernet connection to the Profinet "ET 200S IM 151-3 PN HF", but sometimes the BF (bus error) is flashing with red color. And appears this:
Station status: CF81FD05
Connection aborted: AR consummer DHT expired.
Why happens this problem? Is it possible to connect via Ethernet or do I have to connect via USB with an USB to Ethernet adpater?
either performance issue - reduce reduction Ratio..
or check the task cycle for the profinet io update Task,
it is by default 1ms does this work for BBB?
Log in to post a comment.